|Max. distance||12 m|
|Measured range of temperature||-20… +60°С|
|Maximum distance||200 meters|
|Customs code||8531 10 950 1|
|Mounting||There are mounting slot on the bottom of the case for fastening. Fasten sensor, connect RJ11 connector to the input of the previous CAN unit, sensor or of the monitoring unit. The red LED lights up.
Match the bus terminators of the CAN units. Switch terminator TR in ON position on the monitoring unit and on the last CAN unit or this sensor, TR on intermediate CAN units are in Off (1,2) position. Maximum 8 CAN units, sensors and/or devices can be on one CAN bus.
|Connection||To connect sensor unit to the system, log into the interface -> Preferences -> Can Config -> CAN1 or CAN2 (depends on which physical port CAN1 or CAN2 of the system the unit is connected).
Click Config button and wait. The system will poll the bus CAN and give rows with data, if successful will write: Done!. CAN modules and sensors will appear in the list. Click Apply and then click Restart.
Go to --> System Map / Floor Map, click Refresh button, or wait, new devices and new sensors will appear in the tree. Green LED will light up when CAN sensor is connected and successfully determined by the system.
Connection is not successful if after clicking Config, the poll is reset before the phrase "Updating". Check whether terminators on the bus line are set in the right position, change their position using TR switch if needed.
|Supply includes||Sensor, built in 3-wired shielded patch cable RJ12 (2m), screws, plastic bracket, manual.|